Design and installation
A scientific and rational design of the generator room is conducive to give full play to engage in quality diesel generator set of excellent features to extend the service life and improve its reliability. The standard design and installation of the unit shall include factors such as the weight of the floor, the location of the channel, the location of the maintenance, the connection of the vibration, ventilation, the smoke pipe, the noise of the engine room, the size and location of the fuel tank, Or the country's environmental regulations shall prevail. Also choose the installation site (basement, ground or roof), the level of fixed, to ensure that there is air circulation and operation and maintenance space.
Standard room: general or temporary site, away from the urban and residential areas of the factory, the noise is not demanding occasions.
Environmentally friendly room: close to the residents of the site, factories, buildings and schools, hospitals and other places where the noise is very high.
Standard room: about 90-95 decibels at a meter from the outside of the room.
Environmentally friendly room: about 60 decibels at a meter from the outside of the room.
According to the site selection environment, environmental protection and customer special requirements, the installation of the project options:
1,the generator room interior design, layout and installation;
2, design and installation of the base fuel system, the process of daily fuel system, remote fuel system and integrated fuel system
3, design and installation of the into the wind system and exhaust system;
4, integrated cooling system or remote cooling system design and installation;
5, industrial or noise reduction muffler and smoke system design and installation
6, design and implementation of the control system, the generator unit electrical circuit connection, the unit grounding and other electrical;
7, automatic conversion and parallel control system design and implementation;
8, the generator group noise treatment
9, the generator group of exhaust treatment;
10, fire system design and layout.